> > I'm the new tech guy for a small Christian school in Houston, and we
> > are going to connect a few buildings with fiber (MM plenum duplex
> > zipcord) this week.
I'd get the advice of a capable experienced electrician. Surely
you have the paid or volunteer services of such an individual
available to help you do this right.
Technically, you must comply with NEC (National Electrical Code)
for applicable wiring/cable types when installing this cable.
(And as a school, you'd want to be very careful about complying
with applicable fire and electrical safety regulations.)
Your facility may have plenum ceiling areas, all cables installed in
those areas must be of a type rated for plenum use. Many duplex zip
fiber cables are not, but some are.
Cables run in areas where they can be accessed by humans (typically
less than 8' off the floor) must be in suitable condiut. ABS or similar
non-metallic conduit, properly supported, may be a good choice. Check.
The critcal factor will be the quality of your fiber connector
terminations. Good fiber optic connectors carefully installed,
inspected and tested, using the right tools will make your project
Comment: Fiber cable is not that expensive. Future labor is expensive.
I'd suggest installation of a 6 core fiber cable vs. 2 core fiber zip.
That would provide spare fiber for future use and the cable itself is
better constructed. I'd terminate and test all fibers.
Suggestion: Fiber cable, fiber termination patch panels and boxes show
up on ebay several times a month. It pays to know what you want and
how much it costs. Use a catalog like Mile-Tek as a reference.
Good luck with your project.
Macy M. Hallock, Jr. - APK Net - Tel:216.241.7166 - Fax:216.241.7522